An U.S.A. Corporation
Call Us, We Like Talking To You
Free Shipping On $1500.00 Net Orders
18 gauge stranded copper wire with PVC insulation available in Black, Red, and Green
18 GA Electrode Suspension Wire
$ .29 per foot
BW Electrode systems are one of the best ways to protect your water well submersible pump from running dry and being damaged. B/W relays are placed between your pump power supply and the controls for your submersible pump. From the BW relay, 3 electrode wires are run to the well and down to the electrodes hanging in the well. The lowest electrode is your liquid ground electrode, which goes below the pump, makes certain that proper ground is provided to the other two electrodes. One BW electrode is installed just above the submersible pump as the cutoff electrode. This electrode turns off the power before your pump starts to run dry. The Upper electrode is placed at a level below your static water line, and up from the cutoff electrode far enough to allow recovery time before the pump restarts. Once the water rises to a level where it covers the upper electrode, the B/W relay resets and allows power to go to the pump controls.
Installation Instructions for the "LH" BW Control
This is the standard BW box used for 1 HP or smaller size pumps.
The 1500C sensor control will protect your pump from running dry when the water level drops to a dangerous level in the well.
Proper wiring of this unit is important to allow it to perform properly. The unit is wired between your power source and your pump control box.
The wire from your power source will have 2 wires that are hot with electricity. These will be referred to as L-1 and L-2.
L-1 will connect to the BW terminal #3
L-2 will connect to the BW terminal #4
From the BW #3, install a jumper wire to BW #5
From the BW #4, go into the pump control box to L-2 input
From the BW #6, go into the pump control box to L-1 input
Now it is time to set up your stainless steel electrodes for in the well.
There are 3 electrodes used in the proper installation. It is recommended that you leave the wire above each electrode hanging free in the well, at least 6" to 12" to prevent deposits from forming on the electrode that could cause false readings to the sensor control. It is also recommended that you place a bit of silicone gel on the top of the electrode cover where the wire goes in, to prevent water from getting into the top of the cap and being held there when the water drains from the bottom of the electrode. This will prevent false readings caused by water in the cap.
You may choose to lay out the wires for your electrodes on the ground to get them ready to install in the well. This way, you can measure the distance you desire between the electrodes, and tape the wires together so they hang as a unit. Remember to leave the ends near the electrode free, so it can move with the water.
BW sensor #7 is jumper wired to BW sensor #9.
BW sensor #9 then goes to the upper level electrode in the well. This electrode is the one which resets the control to allow your pump operation after the power has cut off due to low water level in the well.
BW sensor #8 goes to your low level cut off electrode. When the water level drops to the level where this electrode is out of the water, the power to the pump will be shut off.
BW sensor #10 goes to a liquid ground. This should be hung in the well somewhere below the lower level cut off electrode. NOTE connecting this terminal to a ground stake will not provide a proper ground, and may make the control malfunction. Ground must be to liquid.
RH 115V HIGH WATER SHUT-OFF CONTROL
is for use with 115V motors in a pump up to fill tank control mode. The 1500-D-L1 S7 N1 X relay will turn off the pump when the tank or cistern has been filled.
RH 230V HIGH WATER SHUT-OFF CONTROL
is for use with 115V motors in a pump up to fill tank control mode. The 1500-D-L2 S7 N1 X relay will turn off the pump when the tank or cistern has been filled
E1S Stainless Steel Electrode
Call 800-748-1889 for application and design assistance
LH 115V LOW WATER CUT-OFF CONTROL
is for use with 115V motors in a pump down or low water level control mode. The 1500-C-L1 S7 N1 X relay will turn off the pump when a low water level in the well has been reached or when the tank or cistern being used as your water source has been emptied
LH 230V LOW WATER CUT-OFF CONTROL
is for use with 230V motors in a pump down or low water level control mode. Order the 1500-C-L2-S7-N1-X
The BW control uses 3 electrodes to control your pump in the well. The first electrode is the ground to liquid electrode. It will be hung in the cistern below the other 2 electrodes. This assures a proper grounding of the sensor control and proper performance. A ground to a ground stake is not adequate to make your system work right.
The next electrode is above the ground electrode and provides the power on signal when the water level drops below it. This turns your pump on to refill the cistern.
The upper electrode is set at a level of full and turns the pump off when the cistern is full.